As a steam turbine OEM with experience on many types of valves, GE is well qualified to carry out repairs on valves and actuators of any OEM.
GE has established analysis and repair techniques for both temporary and long-term repair solutions. This work can be integrated with a long-term replacement or upgrade strategy.
Rotors are prone to bowing because of many factors, including a reduced number of bearing pedestals and today’s more demanding operating requirements.
GE’s rotor straightening solution includes an engineering root cause analysis, assessment and computer modeling, and recommendations based on the condition of the rotor.
How we repair your rotor:
With over 570 rotor welding projects completed, GE has the experience you can rely on.
Combining outstanding rotor weld experience with world-class technical knowledge, Global Repair Solutions (GRS) has the technical experience to return damaged rotors back into service with both long- and short-term solutions.
GE Power offers a partial steam path repair solution for major steam turbine diaphragm repairs.
As part of the repair process, the damaged exit side of the steam path and sidewalls is machined so that it is returned to the transition point of the partition, typically about one-third of the depth. The removed steam path side is then replaced with new partial partitions and sidewalls.
Diaphragm dishing is a known issue on most steam turbines. It occurs because of elevated temperatures and high stresses, which cause the steel to creep over time.
GE conducted a study to look at several dishing repair methods and the effect they have on long term dishing. Using ANSYS and GE proprietary modeling techniques, the study was performed on typical third-stage HP and IP diaphragms from medium-sized turbines. The results show that GE’s Power Services solution can offer a more than 50% reduction in creep over time vs. a bridge repair, and better results were observed in comparison to pure heat straightening.